the CPC KB · Dissipation / Power Factor and Capacitance Measurement on Rotating Machines using the CPC/TD1 and CR 2 MB. OMICRON. CPC Reference Manual. PRIMARY TEST SYSTEM. FOR SUBSTATION This Reference Manual is a publication of OMICRON electronics GmbH. All rights . View and Download Omicron CPC user manual online. CPC Test Equipment pdf manual download.
|Published (Last):||26 June 2006|
|PDF File Size:||12.95 Mb|
|ePub File Size:||12.51 Mb|
|Price:||Free* [*Free Regsitration Required]|
CPC – Documents – OMICRON
Common Functions Common Functions This chapter describes functions c;c procedures that repeat in all or various test cards. The file containing the up-to-date measurements should be saved regularly. D I T Editor, loads the file and lets you edit it. Introduction View Selector Figure Page AC output range. Any other use of the CPC but the one mentioned above is considered improper use, any voltage potential.
Changing Fuses CPC Setup for a winding Page To do so, CPC injects a special polarity test signal at a certain location. Page A stylesheet contains formatting information, and offers the possibility to influence the presentation of test reports. VTRatio test card with test results Navigate to the parameter fields, and enter the values according to your test requirements: PolCheck test card with test points Navigate to the parameter fields, and enter the values according to your test requirements: Page 13 CPC V 3.
Manhal Quick opens the During operation, the CPC creates a log file with a user-definable logging level. The product c;c, specifications, and technical data embodied in this manual omicfon. If you have a cardiac pacemaker, do not use CPC !
Contents of this section Test Assessment Step 3 Press S Now set the output current value of your choice by turning the handwheel, or use the number keys of CPC soft-touch keyboard. Page Voltage Transformer 2. This is a physical and an electrical hazard.
Omicron CPC 100 Reference Manual
Resistance Test settings Figure 7: Upgrading The Cpc Software. This way, the CPC high-current outputs represent the “amplified” Comments to this Manuals Your Name. A state represents an output quantity with defined settings, for example, a certain magnitude and frequency, for a preset period of time.
Before disconnecting from CPCconnect the device under test to protective earth. The Quick test card enters the “on” state, the set power output value is switched to the CPC outputs, the measuring continues.
Omicron CPC 100 User Manual
After then, a new result line is added showing the number of the next measured tap. At our technical support.
If the focus is on the table, scrolling through the lines will change this display accordingly, depending on the selected line. Furthermore it is used for contact and winding resistance testing, polarity checks as well as primary and secondary protection relay testing.
Page 38 Safety Key Lock To enable CPC entire functionality, put the key into the safety key lock and turn it horizontally to the right as shown in Figure 9. With regard to software handling, this section confines to test-relevant issues, and does not go into detailed procedural descriptions.
Therefore, pressing Sfor example, does not save the test that Options tab Kanual Setup External booster The “External booster” combo box allows to set the external booster: Extended by a high number of valuable accessories the application range of the CPC is further expanded.
Page Others – Ramping Example of a series of ramps Figure The default setting is “Warning”. Deletes the current test card from the test procedure.
Ramping CPC V1. Also the step voltage around the electrode can be quite high. Page 69 OS Version: Page 80 CPC V1. Page Technical Data Table Page 11 Set date and time. There is no according on-screen message shown on the CPC monitor. Page 22 Select to stop test frequency I nominal via an integrating amplifier or fed into an electronic protection relay with integrator.